Meeting ASTM D-2564
Medium viscosity; fast drying;
Mainly used for hard UPVC pipes and joints under
inside nominal diameter under Dn 100.
|UPVC、CPVC、ABS Pipeline Glue|
|Specifications||Coated volume||Number joints 250g||Specifications||Coated volume||Number joints 250g|
|Misuse of glue for first aid|
Inhalation: If inhalation and collapsed ,please move the patients to fresh air; if patients with difficulty in breathing ,give oxygen and requested medical attention.
Eye or skin contact: use of adequate water rinse eyes for 15 minutes, if the aggravating circumstances, please seek medical treatment as soon as possible.
Eating: such eat mistaken, avoid spit and send to hospital for cure.
Adhesive should be stored in 15°C -38°C in the day environment, avoid sunlight, and maintain a period of 2 years(use it as soon as possible afer opening).
|The basic cementation principle for solvent adhesive|
1.Apply preliminary glue to make the pipe and sufficiently soft and soaked with the glue.
2.Use sufficient glue so that the gaps between the pipes and joints are properly filled.
3.Bond the pipes and joints when the glue is wet.
4.Since the ends sustain around 70% of the strength, the pipes must be pushed to the end.
|Bonding technology of pipelines|
1.The ends of pipes must be cut neatly and must perpendicular to thecentral axis of the pipe.
2.Remove he flash in the out of the pipe and chamfer(10 to 15 degrees)
3.Wipe off he dirt, oil stans and moisture in and out of the pipes(since they adversely affect bonding strength)
4.Use measuring instruments to measure the depth of the reception of the joints and mark the measured data on the inserting part of the joints.
5.Start the bonding
1.Firstly, apply the preliminary glue on the joint. It is prohibited to allow the glue to floe into the joints.
2.Then apply the preliminary glue on the scope marked on the pipe.
3.Homogeneously apply glue on the inserting part of the pipe, the applied lenget being the marking scope.
4.Lmmediately afterwards, used the same brush to apply glue onto the receiver of joint.
5.When the glue is wet, immediately insert the joint and use enough force to push it to the end and twist it an twist it an angle of 15 to 45
6.Push the glued connection of the joints, make sure the joints will not be pushed out under static force.
7.Upon the piece of cloth to wipe off the redundant glue at the connecting part.
8.Use a piece of cloth to wipe off the redundant glue at the connectingpaat.
|Five basic coperation methods|
1.The surface for bonding must be properly softened and soaked
2.Sufficient glue is needed to fill the gaps between the pipes and joints.
3.The pipes and joints must be bonded when the glue is wet
4.The pipes and pipe pieces must be pushed to the end.
5.Sufficiet complete solidification time is required for dtying before pressure is applied.
|Time of force sustaining after the application of glue|
|Time offorce sustaining||1||1||1.5||2||2||2||3||3|
|Time offorce sustaining||4||5||8||8||15||20||25|
|Time offorce sustaining||2||4||12||24||30|
|Time requiredfor complete solidification|
|Time offorce sustaining||3||6||8||12|
Note: the above fixed minutes are the experimental date under the normal temperature, while it should be longer in winter.
|Bonding under low temperature|
1.Bonding shouldn't be done in the morning orevening.
2.Store the glue at a warm or normal temperature place to increase its flowability.
3.Wipe off the moisture on the pipes or joints to be bonded.
4.If possible, expose the pipes or joints in the sunlight for several hours.
5.Due to the cold temberature, the drying time is longer than it is under normal temperature. After complete solisification , place it idle for a certain period before applying the pressure
6.Under cold weather ,the pipelines should be bonded section by section to avoid the movement of joints as much as possile.
7.Before the installation, read the pipeBonding Technique carefully and conduct the installation as per the operatin procedure.
|Bonding under high temperature|
1.The glue and preliminary glue shall be stored in a cool room with good ventilation.
2.If possible, the pipes and joints shall be also stored in a cool room with good ventilation.
3.Try to conduct the bonding of pipe shall be done in the morning.
4.Use a wet cloth to wipe the area on the pipes to be bonded. The vaporization of water can reduce the temperature by some degrees how even, before the bonding, make sure the connecting suefaces are completely day.
5.When the bonding is done, make suef the glue is wet. If a pipe with large diameter is to be bnded, the work must be done under cooperation of many people.
6.Use glue with high viscosity for the bonding, because high viscosity glue dries up slowly and promises longer bonding time.
7.After the application of glue, the lid must be put on the container.
1.Always bear in mind that preliminary glue is prohibited for bonding of ABS pipes.
2.Fire is prohibite at the bonding site.
3.Bonding must not be done under rainy or snowy weather.
4.Bonding must not be done when the temperature at site is lower than -20°C.
5.Try to conduct the bonding in an area with good ventilation.
6.Try to avoid contact with skin or eyes.
7.Into contact with the local children.